Series 90*-30 IC693DNS201 GFK-2195E DeviceNet Slave Module July 2011 The Series 90* -30 DeviceNet Slave Module (IC693DNS201) operates as a network server (slave) only. It can automatically exchange PLC data with a network master, and respond to custom explicit messages from the master. Features The DeviceNet Slave Module allows a Series 90-30 PLC to send and receive I/O data from a DeviceNet network. Module features include: ▪ Bus communications at all standard DeviceNet data rates (125K, 250K, 500K baud) ▪ Up to 255 bytes input data transfer and 255 bytes output data transfer. ▪ Support for Poll, Strobe, Cyclic and COS I/O Connections, and Explicit Messaging ▪ Support for Unconnected Message Manager (UCMM) allowing up to 250 simultaneous explicit messaging connections. ▪ Support for the Assembly Object and access to the input and output data for each of the configured slave I/O areas (I/O Area 1 and I/O Area 2) via the SET_ATTRIBUTE_SINGLE and GET_ATTRIBUTE_SINGLE services. Up to 255 bytes of attribute data may be supplied in the SET_ATTRIBUTE_SINGLE operation. ▪ One or two I/O connections plus explicit messaging can be configured. Each I/O connection can be set up for one of the following: Poll, Strobe, Cyclic or Changeof-State (COS) operation. Typically one connection is used for Polled and the other is used for Strobe, Cyclic, or COS. ▪ Configurable fault behavior on loss of communication. ▪ UCMM-capable Group 2 Server Compatibility ▪ Compatible with any Series 90-30 CPU except IC693CPU321 and IC693CPU340. Requires Series 90-30 release 8.0 or later CPU firmware. Release 10 or later is recommended, if available for the particular CPU. ▪ Requires Proficy* Machine Edition Logic Developer PLC version 3.0 SP1 Special 2 or later. ▪ Not compatible with the VersaPro*, Control, or Logicmaster* programming software. ▪ The Series 90-30 Hand-Held Programmer (IC693PRG300) cannot be used to configure this module. ▪ The DNS supercedes the HE693DNT750 slave module for new applications. It may also be retrofitted into existing applications of the HE693DNT750 slave module, but its functional differences must be taken into account. For details, see Operating Notes on page 2. * indicates a trademark of GE Intelligent Platforms, Inc. and/or its affiliates. All other trademarks are the property of their respective owners. All rights reserved. 2 DeviceNet Slave Module GFK-2195E Release Information Release History Catalog Suffix Firmware Version Boot Firmware Version EDS File Version (9030slave.eds) Date Comments CD 1.25 1.00 1.04 Jul. 2011 Label change. No changes to features, performance or compatibility. BD 1.25 1.00 1.04 Jul. 2006 BC 1.22 1.00 1.04 Nov 2004 AB 1.18 1.00 1.04 Dec 2003 AA 1.16 1.00 1.04 Oct 2002 Upgrades This release of the DeviceNet module firmware replaces all previous versions. It is backward compatible with all previous firmware versions of the Series 90-30 DeviceNet modules, IC693DNM200 and IC693DNS201. IC693DNS201 can be field-upgraded to firmware version 1.22 by ordering the upgrade kit below or downloading it from the Support website, http://support.ge-ip.com. Upgrade kit: 44A75223-G02 Fixed in this Release In high-end systems (such as Series 90-30 CPU374), sending several COMMREQs to the module in rapid succession will not cause a backplane communications or loss of module fault in the fault table. Operating Notes Migrating from the HE693DNT750 Module If the IC693DNS201 Series 90-30 DeviceNet Slave Module will be used to replace a HE693DNT750 slave module in an existing application, the following differences must be taken into account: ▪ Configuration: The HE693DNT750 module must be configured via its serial port prior to adding it to the rack configuration of the PLC. No such initial module configuration is required for the IC693DNS201; all configuration is done using the programmer. ▪ Status Reporting: The HE693DNT750 module reports the following diagnostic status information to the ladder program: Bus Fault, Connection Established, and RECEIVE_IDLE active. It reports PLC RUN mode status in the diagnostic byte sent to the scanner. ▪ The IC693DNS201 DeviceNet Slave Module reports the following information to the ladder in the userconfigured location: server status, CAN status, and firmware revision. See the Series 90-30 DeviceNet Modules User’s Manual, GFK-2196 for more information. ▪ Get/Set PLC Registers: The IC693DNS201 DeviceNet Slave Module supports the same Get PLC Registers and Set PLC Registers services as the HE693DNT750 module. ▪ Fault Reporting: Fault reporting in the IC693DNS201 can be disabled to match the behavior of the HE693DNT750. ▪ Serial Port Functionality: The RS-485 port on the HE693DNT750 is used to supply configuration information to the module prior to PLC rack configuration. The RS-232 port on the IC693DNS201 DeviceNet Slave Module is used for firmware upgrades. DeviceNet Slave Module 3 GFK-2195D Specifications: DNS201 Catalog Numbers IC693DNS201 Description Slave Module for DeviceNet networks Mounting Location Series 90-30 main rack: Any slot except slots 0 and 1. Environment Storage temperature: -40C to 85C Operating temperature: 0C to 60C Backplane Current Consumption 450mA at 5VDC (typical) For product standards and general specifications, refer to Product Agency Approvals, Standards, General Specifications, GFK-0867 Installation in Hazardous Locations The following information is for products bearing the UL marking for Hazardous Locations: ▪ WARNING - EXPLOSION HAZARD - SUBSTITUTION OF COMPONENTS MAY IMPAIR SUITABILITY FOR CLASS I, DIVISION 2; ▪ WARNING - EXPLOSION HAZARD - WHEN IN HAZARDOUS LOCATIONS, TURN OFF POWER BEFORE REPLACING OR WIRING MODULES; AND ▪ WARNING - EXPLOSION HAZARD - DO NOT CONNECT OR DISCONNECT EQUIPMENT UNLESS POWER HAS BEEN SWITCHED OFF OR THE AREA IS KNOWN TO BE NONHAZARDOUS. ▪ EQUIPMENT LABELED WITH REFERENCE TO CLASS I, GROUPS A, B, C & D, DIV. 2 HAZARDOUS LOCATIONS IS SUITABLE FOR USE IN CLASS I, DIVISION 2, GROUPS A, B, C, D OR NON-HAZARDOUS LOCATIONS ONLY.