Wiring connections to and from user-supplied input and output field devices are made
to the detachable terminal board supplied with each I/O module. This removable
terminal board makes it easy to pre-wire field wiring to the user-supplied input and
output devices, and to replace modules in the field without disturbing existing field
The I/O terminal boards has 20 screw terminals. Each terminal accepts up to one AWG
#14 wire using ring or lug type terminals. Minimum recommended wire size is AWG
#22. These terminals require a flat or Phillips head screwdriver for installing field
wiring. An isolated 24 volt DC supply is available on the power supply. Wires are
routed to and from the terminals out of the bottom of the terminal board cavity.
Installing a Terminal Board
To install a terminal board with no wires attached:
1. Hook the hinge, located on the bottom of the terminal board, to the lower slot on
2. Push the terminal board toward the module until it snaps into place.
3. Open the terminal board cover and ensure that the latch on the module is securely
holding the terminal board in place.
Check the label on the hinged door and the label on the module to
ensure that they match. If a wired terminal board is installed on the
wrong module type, damage to the module could occur.
When installing a terminal board that has wiring attached, verify that the terminal board
is connected to the proper module type. Figure 2-3 shows the recommended procedure
for terminal board installation.
Figure 2-3. Installing a Terminal Board
Warning: include_once(/js/tracking.php): failed to open stream: No such file or directory in /var/www/series/revision.php on line 248
Warning: include_once(): Failed opening '/js/tracking.php' for inclusion (include_path='.:/usr/share/php:/usr/share/pear') in /var/www/series/revision.php on line 248